NOT part of the instructions yet. This will be incorporated later.
Assuming the following power rating: 2360 watts - 300watts per tower model, 280watts per desktop (incl 1 screen) and 40watts for the KVM
I would like to propose the following:
SUM3000RMXLI2U - APC Smart-UPS XL Modular 3000VA/2700watts 230V
- 2 U rack height
- 82% of capacity used with 2360watts. Recommended not to full 100%
- capacity because is inrush current during start up.
- Network management card with environmental monitoring included with
- the ups
- extended runtime capability
- remote group oulet control
2 x SUM48RMXLBP2U - external battery pack
Tower/Rack Convertible for 39minutes runtime. Without extra battery, 5minutes runtime & with one 19 minutes runtime.
- both batteries 2U rack height